Complete Plant ROTAMAT® Ro5
Manufacturer: Huber Technologies
The Original - with well-proven mechanical pre-treatment components
With aerated or optionally unaerated grit channel
Grit trap design according to DWA or customized
Separate grease trap with semi-automatic grease removal (optional)
For reasons of operational safety the first step of sewage treatment works is generally mechanical wastewater pre-treatment including:
Separation and removal of fat and grease
We developed and supplied our first ROTAMAT® Complete Plant Ro5 during the 1980s. Since then hundreds of consulting engineers and operators have selected and installed our Complete Plants because of their reliable operation and low maintenance. Planning and installation of our ROTAMAT® Complete Plants is not only quick and easy, but also saves considerable construction costs.
1. Fine screening
Depending on the specific conditions and data, such as peak flow, screenings load and grit load, one of the following screens is selected:
HUBER Fine Screen ROTAMAT® Ro1
Bar spacing 6 or 10 mm
HUBER Rotary Drum Fine Screen ROTAMAT® Ro2 / RPPS
Bar spacing 1 - 6 mm
HUBER Micro Strainer ROTAMAT® Ro9
Bar spacing 1 - 6 mm
HUBER Belt Screen EscaMax®
Perforation 1 - 10 mm
HUBER Fine Screen STEP SCREEN® SSF
Slot width 3 / 6 mm
2. Screenings treatment
Fine Screen Ro1 / Rotary Drum Fine Screen Ro2 / RPPS / Micro Strainer Ro9:
All ROTAMAT® Screens include a screenings press.
Screenings washing with IRGA (optional)
Dewatering and compaction in integrated screenings press
Solids concentration of screenings: Up to 45 % DS.
STEP SCREEN® SSF, Belt Screen EscaMax®
A separate HUBER Screenings Wash Press WAP® is usually installed behind the screen.
Solids concentration of screenings, depending on the WAP® type used: Up to 50 % DS.
3. Grit separation
The grit channels of our HUBER ROTAMAT® Complete Plants are designed in accordance with international standards or the customer’s specific requirements. The grit channels are available as aerated or optionally unaerated units. The selection of the grit channel type (aerated or unaerated) depends on various criteria, such as the storm/dry weather flow ratio or whether further grit treatment systems are planned.
4. Grit removal and discharge
The settled grit is collected from the bottom of the grit channel with a horizontal grit screw. An inclined grit screw conveys, agitates and dewaters the collected grit. The classified grit slides from the upper end of the inclined screw into a RoSF4 T Grit Washer.
5. Grease separation and removal (optional)
Separation of fats and grease is only available when used with aerated grit channels. The grease is collected in a separate chamber with the partition between the grit trap chamber and grease chamber consisting of a slotted scum board. In contrast to many competitors, the floating fats and oils are skimmed off the water surface with a paddle scraper that is slowly pulled with a stainless steel rope. The paddle is shaped so that it removes virtually all floating matter from the grease trap. Anaerobic degradation of fat and grease and therefore odour nuisance, is thus prevented.
Complete and compact headwork unit performing the following process steps:
Screenings washing (optional)
Grit trap aeration (optional)
Optional combination with grit washing
Grease separation and removal (optional)
Removal efficiency in accordance with international standards (DWA) with Qmax: 90 % of 75 mesh grit (particle diameter 0.2 – 0.25 mm)
Throughput capacity up to 300 l/s
Separate grease chamber with semi-automatic grease removal (optional)
Completely encased unit, no odor nuisance
Frost protection for outdoor installation (optional)
Above-ground or underground installation
More than 800 installations
Completely made of stainless steel (including the classifying screw)